Heat Air for Drying and Curing Operations up
to 750°F Air Temperature, Heat Treating, Reheating
or Dehumidification, Booster Heater
in Heating Ducts and Ovens.
U-Shaped Tubular Elements with INCOLOY®
sheath are mounted in a heavy gauge steel
flange with 9/32" diameter mounting holes for
attaching to duct work. All terminal connections
are of high-temperature alloy construction
and are enclosed in an aluminum painted
Steel flange is equipped with special holes to
permit easy replacement of individual element.
Sheet steel terminal box may be removed to
facilitate wiring during installation.
All Heaters can be mounted in any position;
top, side or bottom entry. In high ambient
temperature operations, least corrosive action
and least oxidation to the terminals will occur
if heaters are mounted with terminals in the
coolest possible ambient, usually on bottom or side of duct. Minimum duct size is
A dimension plus 3/8" or 11-1/8" plus 3/8"
and B dimension plus 1-5/8".
Wiring — Terminals on field wiring connections
are located in circular junction box
outside of heating zone. Alloy wire or buss bar
must be used for power connections.
Maximum Sheath Temperature — 1150°F.